We provide the high-quality UPVC Foot Valves manufacturer & supplier in India. In what way does a vertical turbine pump maintain its priming pressures? Will gravity not take over after the pump is switched off and run all the water back into your tank once the pump is shut off. Learn how foot valves keep pumps primed and prevent them from harm in this article.
In a suction lift application, UPVC Foot Valve is located at the end of a pipeline. In addition to serving as a check valve, they also include a strainer attached to the open end of the valve.
The check valve has a spring-assisted check valve. Whenever a pump is turned on, the pump column’s tension varies, and the valve opens as a result. Whenever the pump is turned off, the valve responds by shutting once again. As a result, the pump will not lose prime every time it is turned off due to fluid leaking out of the pump column.
The VZ foot valve allows the passage of fluid in one direction only.
• Connection system for solvent weld and threaded joints
• No metal parts in contact with the fluid
• Piston with incorporated counterweight able to work with high intensity
• Limited pressure loss. Only minimum back pressure is required for the
• Valve material compatibility (PVC-U) with water, drinking water and other
food substance conveyance according to current regulations
• Can be maintained with the valve body installed
|Size range||DN 10 ÷ 50|
|Nominal pressure||PN 16 with water at 20 °C|
|Temperature range||0 °C ÷ 60 °C|
|Coupling standards||Solvent welding: EN ISO 1452, EN ISO 15493, BS
4346-1, DIN 8063, NF T54-028. Can be coupled to
pipes according to EN ISO 1452, EN ISO 15493, DIN
8062, NF T54-016.
Thread: ISO 228-1, DIN 2999.
|Reference standards||Construction criteria: EN ISO 16137 EN ISO 1452, EN
Test methods and requirements: ISO 9393
Installation criteria: DVS 2204, DVS 2221, UNI 11242