UPVC Valves also known as PVC Valves are frequently utilized for a variety of household and commercial purposes, including pipe linkages and other applications. Unplasticized Polyvinyl Chloride valves are naturally damage-resistant and are an agriculturalist’s closest ally.
UPVC valves are constructed of good quality Unplasticized Polyvinyl Chloride and are custom-designed to meet the needs of the customers. When it comes to controlling the flow of heavy liquids and grains, UPVC valves are quite effective.
Lead-free uPVC pipes and fittings are non-toxic, simple to install, and designed to provide years of fuss-free service. We also provide a different types of valves like PVC 2 way valve and UPVC 3 way ball valve with all sizes available here.
Liquid commodity delivery via pipeline necessitates the use of a PVC Valve to manage the flow of a fluid. We may observe the use of such valves in agricultural areas where monitoring the water pressure is required to ensure that water is distributed evenly across the agricultural grounds.
These PVC valves can also be utilized in plumbing applications. Irrigation, chemicals, and plumbing are three frequent sectors where such valves are required. UPVC Valves Manufacturer & Supplier company in India.
UPVC Valves Manufacturers in India. We provide different types of Valve Suppliers like- PVC Ball Valve, Ball Valve and Industrial Valves etc. If you want to buy now, click our website.
Solvent welding, or cement jointing, is the longitudinal joining system for connecting rigid PVC-U pipes and fittings. The “cementing” is carried out using adhesives/cements obtained by dissolving PVC-U polymer in a solvent mixture. This solvent liquefies the walls of the pipe and/or fitting, allowing the constituent material to chemically combine and be subse-quently welded. Chemical welding allows permanent joints be achieved possessing
chemical and mechanical strength characteristics identical to those of the pipes and fittings joined. The adhesives/solvent cements must be selected according to the type of thermoplastic resin to weld, in that the nature of the solvents vary, as does
the weld material contained in them. It must be remembered, therefore, that all the solvent cements designed for joining thermoplastic pipes and fittings must be used to join pipes, fittings and valves of the same material.
Before starting any solvent welding operations, the efficiency and condition of the equipment used and the pieces to be assembled must be verified, in particular the uniformity, fluidity and expiry date of the solvent cement.
Cut the pipe perpendicular to its axis to obtain a clean square section, preferably using a wheeled pipe cutter designed specifically for thermoplastic pipes (fig. 1).
Chamfer the outer edges of the pipe in order to ensure that it enters the socket of the fitting at an angle of 15°. The chamfering operation must be carried out at all costs, otherwise the lack of chamfer can lead to the solvent being scraped off the surface of the fitting, thus compromising the effectiveness of the joint. The chamfering must be carried out using the appropriate chamfering tool (fig. 2).
Measure the depth of the socket of the fitting to the internal shoulder and mark the corresponding distance on the end of the pipe (fig. 3 and 4). For more de- tails, refer to the “Socket depth, cement and chamfer length” table.
Using an clean paper towel or applicator soaked in Cleaner-Primer, remove any traces of dirt or grease from the outer surface of the pipe for the entire cement-ing length. Repeat the same operation on the internal surface of the socket of the fitting: leaving the surfaces softened (fig. 5).
Leave the surfaces to dry for a few minutes before applying the solvent cement. Remember that, in addition to cleaning the joint surfaces, the Cleaner-Primer also performs the important role of softening and preparing the surface to receive the solvent, an operation that enables a perfect joint to be obtained.
Apply the solvent cement in a uniform manner longitudinally over both parts to be assembled (outer surface of the pipe and internal coupling surface of the fit-ting) using an applicator or suitably sized coarse brush.
For more detailed information, refer to the “Brush-applicator characteristics and dimensions” table. It is advisable to use an applicator/brush of dimension not less than half the di-ameter of the pipe. The solvent cement must be applied along the entire length
of the joining surface of both the pipe and the fitting:
– for the entire joint length of the pipe previously marked on the outer surface
– for the entire depth of the socket as far as the internal shoulder (fig.7)
Fully insert the pipe into the fitting immediately and without any rotation. Only after this operation will it be possible to slightly rotate both ends (max. 1/4 of a turn between pipe and fitting). This rotation movement will render the layer of applied solvent cement more uniform (fig. 8)
The pipe must be inserted in the fitting as soon and as quick as possible (after no more than 20-25 seconds is recommended). Depending on the external diameter of the pipe and, as a result, possible handling difficulties, the insertion of the pipe
into the fitting must be carried out:
– manually by one person for external diameters < 90 mm.
– manually by two people for external diameters from d 90 to d < 160 mm. – using mechanical pipe-pullers for external diameters > 160 mm.
Immediately after fully inserting the pipe in the fitting, apply pressure to the joined parts for a few seconds. Then use crepe paper or a clean cloth to remove any excess solvent cement from the outer surfaces, and from internal surfaces where possible (fig. 9).
Solvent cement drying: the joined parts must be left to stand in order to allow the solvent cement to set naturally without generating any unnecessary stress. The setting time depends on the amount of stress that the joint will be placed under.
In particular, the following minimum setting times must be respected according
to the ambient temperature:
• before handling the joint:
– from 5 to 10 minutes for ambient T. > 10°C
– from 15 to 20 minutes for ambient T. < 10°C
• for repair joints on pipes of any size or pressure not subject to hydraulic testing:
– 1 hour for each atm of applied pressure
• for joints in pipes and fittings of any diameter subject to pressure testing up to
– minimum 24 hours
The solvent cement setting times indicated are valid at ambient temperature
(approx. 25°C.). For particular climatic conditions (humidity, temperature, etc…),
we recommend you contact our technical services department and/or the solvent
cement manufacturer for more information (fig. 10 and 11).